The device serves as a transparent converter of Ethernet physical layer to MBUS, allowing remote readings of energy meters via LAN network. The converter supports the MBUS layer (also known as M-BUS or Meter-BUS) in accordance with EN 13757-2. The device is made in a plastic cover for mounting on a DIN rail
The device can be powered by a direct supply voltage in the range of 12 to 24 V. It is capable of communicating with up to 60 MBUS slave devices. The maximum length of the cable segment to the slave device can be up to 1000 m at a communication speed of 300 bps. To simplify the management of TCP/IP packets in the parent system, you can use the COM Port Redirector (RFC2217) utility to redirect TCP/IP packets to Virtual COM Port, or connection to OPC server.
For more information see the user guide in the “Download” section.